Adon provides a full range of heating and air conditioning services to the residents of Celina, TX and the surrounding areas. We pride ourselves on providing expert work and outstanding customer experience!
Read our reviews and find out why your neighbors call us for all their heating and air conditioning needs in Celina, TX.
for Celina, TX
Our Reviews by City
Awesome service, again!
Terrance - Celina, TX
Awesome service, fabulous price
Jones - Celina, TX
Couldn't have asked for anything better. Charles was on time, honest, respectful, clean, worked quickly and accurately. Awesome service.
Clean and seal boots to prevent future growth. 1 in Entryway, 1 in front dining room, 1 in living room, 1 in upstairs bedroom (first bedroom on the right). Pictures included
Performed heating tune-up on 2 systems. Found a couple areas of concern, please refer to estimates. Systems are heating properly and safely.
Assist with heat strips
Cooling AC system repair Found that thermostat wire from thermostat to air handler Loss of communication. Common wire to thermostat was barely in the wire not connected to the other common wires. Picked another pair of thermostat wires from Air handler to thermostat. Remove thermostat wire that was zip tied to the high-voltage lines. This is bad on communication wire will induce a voltage Causing bad communication . Unit is operational and cooling at this time
Cooling AC system repair Found evaporator coil frozen due to extremely dirty filter, removed filter and used furnace to thaw coil. No other mechanical failures found at this time. Instructed tenant to change filter once per month due to children and pets in home.
Performed service check on D/S system and found outdoor run capacitor reading 0.003/40 (compressor) and 0.0/5 (fan). Client wished to replace with Turbo200 (S#81991357) to have 5 year part warranty on run capacitor. Tested system operation and found no further issues.
Cooling HVAC system maintenance Performed Tune up and found some areas of concern. No float switch (water damage prevention switch) on drainline, dryer vent very dirty and is causing fire hazard, as well as outdoor control wiring is not protected from elements, animals, and/or machinery. No mechanical failures.
A/C repair for the Jones family, Celina
Found u/s unit flat on refrigerant, put enough refrigerant in system to leak search. Found compressor oil on condenser, sniffer hit on condenser where oil is located. System has been condemned as not repairable, waiting on warranty company to decide if they are replacing equipment or offering cash out.
A/C repair for the Cave family, Celina
Jeff issacs condenser