Call Adon at (903) 482-4900 when you need heating and air conditioning solutions in Fairview, TX! Our family-operated company is ready to help with all your HVAC needs.
See our reviews and learn why our customers in Fairview, TX choose us over and over again for their heating and air conditioning services!
for Fairview, TX
Our Reviews by City
Sandy Dolin - Fairview, TX
Alex Rushing came out and did an excellent job! He went over and above to explain everything about the issue we had with our AC. He thoroughly went through everything that needed to be done, how it would be done and how we need to maintain the system. We would highly recommend the company and Alex Rushing for Great service!!
Neil - Fairview, TX
The crew was on time, worked hard, very polite and considerate of our needs as they did their job.
Johnson - Fairview, TX
Melissa - Fairview, TX
VIP member. Fall tune up for 1 system. Please collect $145
Found drainline clogged, cleared, made adjustments to secondary line (per code), installed float switch (per code). Insulated primary drainline per code. No further issues.
Duct cleaning Clean all ductwork and treat with antimicrobial fog.
Johnson duct cleaning
Performed spring inspection. Drain line is clear at this time. Drain pan bottom is completely clear. Top has only slight wear, functioning 100% at this time.
Spring maintenance for the Johnson family, McKinney
Verified restriction by checking operating pressures. Pump down refrigerant into condensing unit and evacuated line set where repairs were needed. Replaced TXV, piston, and Bi-Flow filter drier. Pressure tested with nitrogen and bubble leak checked work areas. Vacuumed system to required levels. Ran system and checked refrigerant level. Unit is operating correctly at this time.
Performed a one One system AC cooling tuneup
Arrived on location customer present. Replaced flue pipe, cap and rain guard on both furnaces from the roof. Fixed flue pipes to proper angle inside attic for both units. Replaced drain pan 30 x 30 on smaller unit/master bedroom unit. Installed pan float switch on both units. Installed T6 thermostat for master bedroom unit to regular type. Replaced 3 filters; 20x30x1, 20x20x1, and 20x20x1. Units are properly working at this time.