Adon brings residents of Gunter, TX high-quality heating and air conditioning services with a focus on professionalism and amazing customer service!
Our customers in Gunter, TX trust and rely on Adon for their residential and commercial heating and air conditioning. See what their reviews have to say!
for Gunter, TX
Our Reviews by City
John - Gunter, TX 75058
Professional. Friendly. Explained everything.
Taylor - Gunter, TX 75058
Alex was a true professional and was very clear in describing our AC issue. He came out to the house at 11 pm on a Saturday night and was able to solve the problem efficiently. He also thoroughly explained all my options pertaining to fixing the problem, which was greatly appreciated.
Outstanding service and quick response times!
Penny - Gunter, TX 75058
Clarence was knowledgeable and incredibly helpful. He quickly diagnosed our issues and got them fixed just as quickly. Very friendly and professional service!
AC technician A.
AC Maintenance, tune up. Performed cooling maintenance on a 2015 Lennox heat pump and air handler. During my inspection I found that the capacitor on the outdoor unit was getting weak. I informed the customer of it and he wants to wait to replace it at this time. Everything else is functioning properly at this time.
Dual heat system maintenance and repair. Heat system repaired and ready for cold weather.
Ac repair man, air conditioning repair, ac company
HVAC repair in Gunter TX
Performed service on HVAC Propane Furnace in Gunter TX.
Found heat sequencer failure on unit, replaced with part on truck.
Heater repair for Wanda, Gunter
Encourage service by your tech today
Repair thermostat wire from wall to condensing unit. Checked unit to verify it was operational. Unit is clean and operational at this time
Performed service check and found drainline clogged, emergency drain pan float switch almost did not stop water from getting on ceiling. Highly suggest an inline float switch on primary drain line as well as adding an emergency drain line going to outside of home.
Cooling AC system repair Replaced breaker at Air handler for downstairs unit. Replaced secondary pounds on both units. Sealed air leaks on air handler leaking in from attic. Found unit operating in low stage instead of high stage on air handler corrected and now unit is operating at full blower capacity. Ran water down evaporator drain line and it is draining at this time. Clean black growth outside of air handler. Evaporator coilâ€™s were clean at this time. Rinsed out condensing coil with water. Unit is operational and cooling at this time
Cooling AC system maintenance Clean 4 mini split heads and condenser coils, order tool needed to clean heads in place. 7/6/20 Cleaned 4 of 5 mini split heads and cleared drain lines to insure proper flow, customer has two maintenance visits remaining. All units cooling and no water leaking down walls.
Performed a one system heating inspection. Replaced old thermostat with new one at club price. Verified thermostat was operational and turn unit on and off. Washed out condensing coil and checked electrical components. Drain line is clear at this time. Unit is operational and working at this time