Adon provides a full range of heating and air conditioning services to the residents of Richardson, TX and the surrounding areas. We pride ourselves on providing expert work and outstanding customer experience!
Read our reviews and find out why your neighbors call us for all their heating and air conditioning needs in Richardson, TX.
for Richardson, TX
Our Reviews by City
Amazing Service and Super Friendly!
LiL Hooper - Richardson, TX 75081
Charles was on-time and patiently hung out until I arrived. I appreciate it! He introduced himself, played with my dogs, begin working. Very efficient in what he did and was done with work in a timely manner.
Best AC repair in Richardson. Compressor was not coming on. Found a bad buss fuse causing the system to not get the proper voltage supply. This is a 3 phase system so i could not replace the disconnect. Replaced and now system is cooling at its best.
AC system replacement
Performed heating tuneup on gas furnace system. No issues found. System is heating properly.
Performed fall maintenance on two units, no mechanical failures found at this time. Pointed out missing code items, recommended blower assembly cleanings. Customer to speak with spouse about updating equipment.
Duct cleaning plus
Found fuse blown in A/H due to home owner installed Nest thermostat. Recommended VIP service agreement. Replaced blown fuse, customer to program thermostat after it charges.
Century Supply, special order motor.
Found contactor we installed two weeks ago bad and replaced under in-house warranty. At the request to customer replaced nest thermostat with T6 Honeywell thermostat. Checked cooling fan operation due to the house being 90Â° could not test heat. If customer has issues he will contact us .
Cooling AC system repair Found bad blower capacitor, replaced with new 10 mfd. Found bad contactor, replaced with new. Wired up Nest thermostat and confirmed operation.
Cooling HVAC system 8 vents and 1 return. Misc. hvac service charge is for previous duct job done. Client is happy and no longer has noise issue.
Cooling HVAC system maintenance Performed service check, found outdoor run capacitor for D/S main unit was very weak, causing outdoor fan to fail. Found U/S unit ductwork and blower assembly dirty, client wants to schedule cleaning.
Spring tune up for 1 system. Please collect $145. Sold by Glenna. Performed spring maintenance on one system, no mechanical failures found at this time. Quoted UV Light to improve indoor air quality.
Spring maintenance for the Hooper family, Richardson