Whether it’s keeping you comfy in summer heat or winter cold, Adon has all your heating and air conditioning solutions in Whitewright, TX and the surrounding areas!
Our customers in Whitewright, TX love our heating and air conditioning work. But don’t take our word for it! Read the reviews below to see for yourself.
for Whitewright, TX
Our Reviews by City
Great service by professional, knowledgeable techs
Scott - Whitewright, TX 75491
Frank and Zak are both extremely knowledgeable techs who present a professionalism not seen in most representatives of companies today. I am extremely satisfied with your company if they are a reflection of the caliber of quality and knowledge that your techs hold. Two great techs that you are fortunate to have representing your company. Great job- extremely pleased.
AC technician A.
AC repair. New Thermostat, house was not cooling, old thermostat went bad. Adon Complete Air Conditioning and Heating replaced thermostat now cooling perfect
Project proposal for commercial business in Sherman Texas. Thank you for choosing Adon on your Train comfort specialists
Furnace repair for the McIntyre family, Whitewright
Found d/s unit to have a failed 80/5 mfd capacitor, put on turbo to get unit running only to find unit low on refrigerant. Customer asked for quotes to replace both units, did not want to leave capacitor on unit. Gave multiple quotes for customer to consider.
Performed service check and found outdoor unit leaking refrigerant from coil ( non-repairable), coil would take 6-12 weeks to be delivered. Client is thinking about replacing outdoor unit. Wants to talk with wife before continuing.
Cooling AC system repair Performed inspection on heating and cooling. Washed out condensing coil with water. Checked electrical components. Found electrical heat kit working. Blower capacitor is good at this time. 45/5 capacitor on condensing unit was faulty and replaced. Checked Freon levels. Install Armor flex on suction line.Unit is operational and working at this time it is cooling and heating.
Found burnt wire from capacitor common to contactor, replaced wire and checked operation of unit. No other mechanical failures found at this time. Unit is very old and in poor condition due to lack of regular maintenance. Recommended upgrading to new, more efficient equipment and VIP service agreement. Quotes included with invoice.
Cooling AC system maintenance Found ants in contactor, not allowing line voltage to unit. Blew ants out with high pressure air and confirmed operation. Tenant made aware of lack of float switch protection on unit.
Confirmed Return and supply account. 11 Supply and one return. The Bohn approved duct cleaning and checking a few things on the system. Emailing estimates for VIP UV light float switch and coil clean. Mr. Bohn currently most interested in quail clean. Clean in place will need to plastic drip pans to assist and clean repair.
Pull and clean evaporator coil to keep system from freezing up. This does not include refrigerant charges if outdoor unit cannot be pumped down. Replace all burn conatactors to prevent future break downs Install drainline to keep water from rusting outdoor unit further. Installed Float switches. Sealed up D/S unit ductwork with mastic. Tested equipment. No further issues.
Indoor air quality Clean under unit (debris), inside unit (organic growth), and blower assembly
Performed spring maintenance on one system. No mechanical failures found at this time.
A/C repair for the Akin family, Whitewright
Found drain line to outside stopped up. Cleared drain line with nitrogen. Customer has a club membership at this time. Will need to schedule spring check in a month or so