Adon provides a full range of heating and air conditioning services to the residents of Howe, TX and the surrounding areas. We pride ourselves on providing expert work and outstanding customer experience!
Read our reviews and find out why your neighbors call us for all their heating and air conditioning needs in Howe, TX.
for Howe, TX
Our Reviews by City
Ryan - Howe, TX 75459
Excellent Team: from firat contact to on site service!
Tommy - Howe, TX 75459
The best of the best
Heat pump repair on heat strips
Fall maintenance for the Swindell family, Howe
Performed fall tune up on one unit, found defrost control board failure on heat pump. Unit under warranty until 2029. Replaced defrost control board and tested operation. Recommended surge protection and VIP service agreement. Customer stated he would sign up during spring and plan for surge protector.
Fall maintenance for the Kolb family, Howe
Cooling HVAC system maintenance Run capacitors have been discounted $100 each as the new motor will require a new run capacitor of a different size. Cleaning is recommended before installing replacement motor as dust/debris reduces life expectancy of motors. Found other areas of concern. Noted in estimates as well as tune-up forms. Used $39 special spring tune ups instead of $25 off repair - value of $40.
Coil cleanings included with service agreement.
Found unit completely flat on R22. Quoted 14 SEER and 18 SEER heat pump complete system change out. Will credit service charge towards install of complete system.
Client informed Tech of dirty filter that was removed from system and that the unit had frozen up. Checked for water damage around indoor unit, found none. Tested refrigerant levels and found slightly low. Added 1 lb R-22 and verified system cooling. Informed client to keep an eye on filters and replace every 30-45 days to ensure system does not freeze again. Freezing of indoor coil can lead to leaks in system.
13 supply ducts and 1 return duct cleaned with Roto-Brush Beast. (Return before and after picture on file).
Performed spring maintenance on one system, no mechanical failures found at this time. Moved thermostat per customer request and changed all three air filters dated and signed.
Recharge with R-410a